The CR295X is a small, low-cost datalogger that reads input from one or two sensors, then transmits the data using the GOES satellite transmitter. Multiple CR295Xs can be configured as a network, or units can be deployed individually. CRBasic, its full programming language, supports simple or complex programming and many onboard data reduction processes. It supports stand-alone operation in harsh, remote environments.Read More
For new projects, the CR300-series dataloggers are recommended instead of the CR200X-series dataloggers. The CR300-series builds on the successful features of the CR200X-series dataloggers, while adding new features. The CR200X-series dataloggers will continue to be available for customers with existing CR200X networks until 16 January 2018. Refer to the CR200X-Series Datalogger Discontinuation Notice for details.
The CR295X includes an additional RS-232 serial port that allows communications with the TX320, TX312, or SAT HDR GOES satellite transmitter. It has several input channels for measuring a variety of sensors. Gas discharge tubes provide rugged electrostatic discharge protection for the inputs.
The CR295X does not make differential measurements and is not compatible with SDM devices, multiplexers, or thermocouples. (Refer to the Compatibility information on the web page for compatible sensors, peripherals, and software.) Recalibration services are not offered for the CR295X dataloggers.
|-NOTE-||Note: Additional specifications are listed in the CR200X-Series Specifications Sheet.|
|Maximum Scan Rate||1 Hz|
|Pulse Count Channels||2|
|Switched Excitation Channels||2 voltage|
|Communication Ports||2 RS-232|
|Switched Battery Port||1|
|Input Voltage Range||0 to 2500 mV|
|Analog Voltage Accuracy||±(0.25% of reading + (1.2 mV)x(offset)) at -40° to +50°C|
|Analog Voltage Resolution||0.6 mV|
|Operating Temperature||-40° to +50°C|
|Power Requirements||7 to 16 Vdc|
|Typical Current Drain||
|Protocols Supported||PakBus (leaf node only), SDI-12|
|Dimensions||14.0 x 7.6 x 4.8 cm (5.5 x 3.0 x 1.9 in.)|
|Weight||242 g (8.5 oz)|
|Final Storage||512 kB of flash memory for approximately 125,000 data points|
|Operating System||106 kB of flash memory|
|Intermediate Storage||8 kB of SRAM for communication buffers, calculations, variables, etc.|
The CR295X is compatible with our TX320, TX312 (retired), and SAT HDR GOES (retired) satellite transmitters.
The CR295X can communicate with a PC via direct connect, NL201 Network Link Interface, NL240 Wi-Fi Network Link, MD485 multidrop modem, and digital cellular modems. Data can be viewed on an iOS device, an Android device, CD295 DataView II Display, or a user-supplied PDA. To use an iOS or Android device, go to the Apple Store or Google Play and download our LoggerLink Mobile Apps free of charge. User-supplied PDAs require either PConnect or PConnectCE software.
Campbell Scientific’s SDM devices and multiplexers are not supported.
Typical power supply is a BP12 12 Ahr or BP24 24 Ahr battery, CH100 or CH200 regulator, and an SP10 or SP20 solar panel. The CR295X includes a cable for connecting it with the satellite transmitter and power supply.
An ENC16/18 enclosure can house the CR295X logger, satellite transmitter, and power supply; smaller enclosures cannot house the power supply required for GOES communications. Hardware is included with the datalogger for mounting to an enclosure backplate.
The CR295X can measure a variety of sensors including SDI-12 sensors and 4 to 20 mA sensors. It cannot make differential measurements and is not compatible with the freezing-rain/ice, fuel moisture/temperature, geographic position, present weather, soil heat flux, soil matric water potential, and strain sensors listed on our price lists.
The currently available sensors that the CR295X can measure are shown below:
The CR295X is compatible with the following software packages:
Execution of this download installs the Operating System and Compiler on your computer for the following dataloggers:CR200X, CR206X, CR211X, CR216X and CR295X. It also updates the support files for the CRBasic Editor.
Note: Newer CR206X dataloggers (serial # ≥ 19122) and newer CR211X dataloggers (serial # ≥ 19143) have 250 mW radios that must use OS 3 or higher for their datalogger operating system.View Update History
Number of FAQs related to CR295X: 37
Expand AllCollapse All
Not directly. If the CS15-L is connected to a CR200(X) datalogger, the datalogger can take the ac measurement and control a solid-state relay based on some threshold within the datalogger program. The solid-state relay can then control other relays, solenoids, or motor starters. (Use of a solid-state relay is preferred because the datalogger can trigger it with a small 5 Vdc mA signal.) For more information, see the “Measurement and Control Peripherals” section of the operator’s manual.
Current dataloggers compatible with the BMP5 Direct SDK are the CR200X-series, CR1000, CR3000, CR800, and CR850.
Retired compatible dataloggers include the CR10X-PB, CR23X-PB, and CR510-PB. These dataloggers must have the optional PakBus operating system installed, which is available on the Downloads page of our website.
Technically, the SRM-5A is compatible with the CR200X-series dataloggers, but it is more complicated to use it with these dataloggers. To use a SRM-5A with a CR200X-series datalogger, the SRM-5A must be in the DTE position on the station modem. In addition, user-supplied adapters and gender changers are needed to complete the connections between the SRM-5A and the RS-232 port of the datalogger. Contact Campbell Scientific for more information.
Yes. The simplest method is to use conditional program statements that execute most of the code based on time. For example, the data could be scheduled to log at 6 a.m. and finish at 8 p.m. using CRBasic instructions such as IfTime(). Another option is to use an IfThen/EndIf construction that does a logical test of light-level measurements based on a light sensor. An additional option is to use calculated sunrise and sunset times along with a combination of RealTime() and Case instructions.
For more information, see the “Decisions, Decisions, Decisions…” article.
If small amounts of data are transferred per transmission, it will not be a problem. Larger amounts of data can overrun buffers in the modem, causing lost data. In that situation, lower the baud rate on the datalogger to avoid the issue.
The maximum cable length depends on the interface being used.
A datalogger can be programmed to initiate data transfer by using the SendVariables() or ModemCallback() instruction in CRBasic.
NOTE: These instructions are not supported in the CR200X operating system.
No, because it would not work. The SC32B is used to do the following:
The available COM ports listed in the COM Port drop-down menu are supplied to PC400 by the Windows Operating System (OS). If there are no COM ports shown for selection, it most likely means that there are no COM ports registered with the Windows OS. This can be confirmed using the Windows Device Manager (Control Panel | Device Manager | Ports).
Most modern laptops are not equipped with native RS-232 COM ports. In this situation, a USB-to-RS-232 adapter cable must be used to connect to the datalogger. Even when the drivers for this device have been properly installed, the derived COM port will not be shown for selection until the cable is attached to the laptop.
The CR200X-series and the retired CR200-series dataloggers are NOT compatible with SDMs or multiplexers. If more channels are needed or may be needed in the future, consider purchasing a CR800, CR850, or CR1000 instead.